RETROTEC 6222F Lower Leak Pro
Adding the Hard Panels decreases set up time and makes the test easier to run. Yes, it’s the most expensive but those using this system report that it has paid off quickly.
Request literature on all of Retrotec systems to determine the size of enclosures that can be tested with each system.
Test for hold times in flooded volumes up to 102,000 cu ft (2000 m3) for Inert agents and 140,000 cu ft (4000 m3) for halocarbon chemical agents.
Testing pressure relief vents will require more power however. This system will test the venting for a volume up to a maximum of 24,000 cu ft (660 m3) for Inert agents although vents up to 16 sq ft (1.6 m2) can be measured individually.
All Retrotec systems include tech support from Retrotec who originated the idea of Enclosure Integrity testing in 1984. They promoted it within NFPA and in 1986 wrote the first Enclosure Integrity standard. Retrotec has been the lead researcher for enclosure testing ever since. Every major clean agent system manufacturer worldwide relies on Retrotec’s expertise for both hold time and peak pressure predictions.